In this episode of The A-Z of Damp from Atlantis Damp & Timber Proofing Specialists, B is for…..Builders Beware.
Our Property Survey
Atlantis Damp Proofing recently sent our expert surveyor to survey a local property near Knutsford, Cheshire. The property was a beautifully renovated cottage, which had obviously had a lot of investment put into it. Unfortunately, there were signs of decorative spoiling on the walls, suggesting that a damp issue was present. (more…)
G is for….. Garden in your Gutter (causing internal damp)
In this episode of The A-Z of Damp from Atlantis Damp & Timber Proofing Specialists . G is for…… Gardens in your Gutter (causing internal damp).
We recently visited a property in Northwich, Cheshire to survey for damp detected on walls internally. A young family had been quoted over £5,000.00 to remedy a reported rising damp problem in their home. They felt this quote was too high and as such were getting some comparisons. One of their friends recommended speaking to us to get a reliable, honest advice from a CSRT expert.
They were right to get a second opinion. There was no rising damp. Using a surface moisture meter, it was identified that there were no readings at skirting board height, or up to a meter high (which would be typical of rising damp). There were, however, high moisture readings. These were in the corners of the rooms at both the front and back elevations on the ground and first floor at ceiling height. An external inspection revealed that the gutters were severely blocked with debris. There was green staining and algae on the wall next to the downspout. This fault corresponded exactly to the dampness that was detected internally.
Strictly Necessary Cookies
Strictly Necessary Cookie should be enabled at all times so that we can save your preferences for cookie settings.
If you disable this cookie, we will not be able to save your preferences. This means that every time you visit this website you will need to enable or disable cookies again.